Installation Methods of External, Exterior and Outdoor Lighting System includes lighting equipments luminaires, control gears, panel boards, poles, brackets, cabling, and allied minor civil works. All installations are to be carried out under strict supervision of qualified supervisors and engineers. If installation required heavy vehicles, extreme care has to be taken for preventing damages of lighting equipments, control gears and poles.
Standard Commercial Products for External and Outdoor Lighting System to be chosen as per the design requirement specified in the project documents including recommended and approved list of manufacturers.
Standard Commercial Products for Road Lighting Luminaires to be chosen as per the design requirement specified in the project documents including recommended and approved list of manufacturers.
Quality Assurance and Standards for External, Exterior and Outdoor Lighting System to be designed, installed and tested all in accordance with the recommendations of IEC, CISPR and Local Authority.
Submittals for External, Exterior and Outdoor Lighting System consists equipment data, compliance statements, shop drawings or construction drawings, samples, product certificates, field test reports, maintenance data and as-built (record) drawings.
External, Exterior and Outdoor Lighting System includes lighting units with luminaires, lamps, ballasts, poles / support structures, and accessories and related power distribution and control, protective earthing and related builder's work including column foundations, cable pits, cable trenches and ductwork.
It will be the Developers responsibility to obtain all necessary approvals from Authorities having jurisdiction for temporary connections to existing infrastructure. Temporary utilities shall be installed in such a manner as not to interfere with permanent construction.
The scope of this specification covers the supply and installation of lighting fixtures applicable to internal and external places of a building. Work includes, the collection, handling, installation and commissioning of the fluorescent, incandescent, chandelier, mercury vapour lamp light fixtures.
This method of statement specifies the detailed requirements and procedures for the installation of Power and Lighting System Wiring. Installation: No wiring be carried out until the appropriate tests required or in the electrical testing section have been done and the consultant has given his clearance for wiring to commence. A loop in form of wiring shall be used as far as practicable or unless otherwise indicated. Joints in conductors shall be made using insulated terminal blocks complying with requirements of this specification.
Earthing Cables: Separate protective earthing cables for lighting column circuits are to be run with power circuit, terminated at LV supply position in lighting control panel and looped into column earthing terminals. The last column is to be bonded via an earthing bolt to a single 16 mm diameter stainless steel rod, 3.6 m long, driven into ground adjacent to column. Bonding is to be 16 mm2 stranded bare copper conductor.
Main earthing bar is to be provided in main distribution room and connected to earth electrode by 2 insulated conductors (minimum 150 mm2) via testing joints. Earthing bars of main distribution boards are to be connected, by insulated earthing conductor, directly to main earthing bar at main distribution room.