This article covers the manufacture, supply, installation, testing and commissioning of 415 volts, 3 ph, 4 wire, Diesel Alternator Set (Diesel Genset). The set shall be mounted on common base frame and complete in all respects including the auxiliary equipment such as battery auxiliary, lube oil pumps, filters, oil storage tank, centrifuge, etc. including piping required for interconnection between the set and the auxiliaries which are mounted separately.
The scope of this specification covers the supply, installation, testing and commissioning of an Automatic Fire Detection and Alarm System including wiring. All materials and equipment used in the work shall be ISI approved and installed with a high degree of workmanship. The installation as a whole shall comply in all respects with ISI code of practice for Automatic Fire Alarm System (IS 2189-1976) however, contractor shall comply with the latest or superseded versions of IS/BIS to be used for the complete work.
This article explains electrical power cables used in construction works complete with supply, installation, testing and commissioning of High Voltage (HV) and Low Voltage (LV) cables. All cables shall conform to standards of IS 7098-1973, IS 1554-1976 and wiring cables to IS 694-1977 however, contractor shall comply with the latest or superseded versions of IS/BIS to be used for the complete work.
At the completion of the electrical installation works, the entire installation shall be subject to the test before final placing in service under the full responsibility of the contractor. Unless Otherwise specifically called for all tests shall be carried out in conformity with IEE regulations. Contractor shall coordinate with the Client and the Supervising Engineer to get electricity from the local supply authority before starting of testing and commissioning.
The scope of work shall cover laying, connecting, testing and commissioning of low voltage power cables complete with all cable support, cable, cable trays, clamps and joints. Cables to be purchased from who regularly engaged in the manufacturer of electrical cable and wire products of the types and ratings required, whose products have been in satisfactory use in similar service not less than 5 years. The standard of the cables shall comply with National Electrical Manufacturers Association of local standards or any other approved.
Low Voltage Switchgear are familiar to every people since they are the controlling mediators between low voltage utilities and equipments with human beings. Be it a common home DB or an isolator or control centres, they all are being manufactured to use untrained people ie., common people. The scope of works shall cover the supply installation, testing and commissioning of main and sub-distribution boards, panel boards, fusible safety switches, circuit breakers etc. Associated minor building works require for the erection of the distribution boards and panels shall be included in the scope of work.
Electrical wiring needs expertise attention to every building projects. It directly related to the safety of human beings and utilities / equipments people handle. The scope of electrical wiring shall cover supply, installation, testing and commissioning of all conduits and accessories, wiring, switches, socket outlets, junction boxes / pull boxes, GI pull wires, ceiling roses making connections etc. Unless otherwise indicated wiring shall consist of PVC insulated copper conductor wires installed in heavy gauge steel galvanized conduits.