The scope of this specification covers the supply and installation of lighting fixtures applicable to internal and external places of a building. Work includes, the collection, handling, installation and commissioning of the fluorescent, incandescent, chandelier, mercury vapour lamp light fixtures.
Signal and Communication Systems: For telephone, alarm, voice and data, and other communication systems, provide 16 mm2 minimum insulated grounding conductor in raceway from a separate grounding electrode clean system to each service location, terminal cabinet, wiring closet, and central equipment location.
This statement is written for the purpose of establishing method and procedures for the Installation of DB, SMDB and MDB. Installation: To make sure that the entire installation is in conformance and in accordance with the design intent of the project for the Electrical and Low Voltage System in addition to the specification and as per approved shop drawings and comply.
This method statement explains the detailed requirements and procedures for the installation of PVC Conduits and accessories in the concrete slabs, columns, block works and concrete walls. This method statement should be used for both inside and out side the building.
Fire alarm systems have become increasingly sophisticated and functionally more capable and reliable in recent years. They are designed to fulfil two general requirements: protection of property and assets and protection of life. As a result of state and local codes, the life-safety aspect of fire protection has become a major factor in the last two decades.
Method Statement For Installation Of Galvanized Conduits that has to be installed on the Exposed Surface of a building is described here. This method of statement specify the detailed requirements and procedures for the installation of Galvanized Conduits for the exposed surface installation requirement for MEP services of the above building.
Main earthing bar is to be provided in main distribution room and connected to earth electrode by 2 insulated conductors (minimum 150 mm2) via testing joints. Earthing bars of main distribution boards are to be connected, by insulated earthing conductor, directly to main earthing bar at main distribution room.